Parameters Customer stories Downloads Related products Local distributor. Genpower, based in Turkey, designs and manufactures innovative generator systems using natural gas, LPG, bio diesel, bio gas and heavy fuel for export across the world. The reliability of the paralleling capability and the overall controller flexibility, including the ability to customize screen information are invaluable tools in the successful delivery of key infrastructure for one of the most logistically challenging events in the world of sport. Case studies. Case study The Greenest Datacentre in Switzerland. Single gen-set controllers.
|Published (Last):||12 June 2018|
|PDF File Size:||12.63 Mb|
|ePub File Size:||4.39 Mb|
|Price:||Free* [*Free Regsitration Required]|
Remote control InteliLite controller can be remotely controlled. In case of the work on the gen-set check, that nobody can remotely start the engine.
Some of InteliLite functions are subject of changes depend on SW version. The data in this manual only describes the product and are not warranty of performance or characteristic. Software IL-NT 1. ComAp does not assume any responsibility for its use unless otherwise expressly undertaken. Note: SW and HW must be compatible e. Dangerous voltage In no case touch the terminals for voltage and current measurement!
Always connect grounding terminals! Adjust set points All parameters are preadjusted to their typical values. The following instructions are for qualified personnel only. To avoid personal injury do not perform any action not specified in this User guide!!!
InteliLiteNT controllers are equipped with a powerful graphic display showing icons, symbols and bar- graphs for intuitive operation, which sets, together with high functionality, new standards in Gen-set controls.
InteliLiteNT provides gas engine support without ventilation. The key feature of InteliLiteNT is its easy-to-use operation and installation. Predefined configurations for typical applications are available as well as user-defined configurations for special applications.
What is in the package? This is required for computer or Modbus connecting. Card inserts into expansion slot back on the controller. To insert the module, you must open the cover first use screwdriver to open and then insert the module into slot.
Once you have insert it, the module will snap under plastic teeth. It is supposed to be installed permanently. Should you need to remove it, the safest way is to remove whole back cover and than remove module manually. Insert a screwdriver into the slot of the cover. Move the screwdriver to set apart the small cover. Be careful!
Remove the small cover. Break apart the small cover into two pieces. Do not throw away the smaller part! Take RS communication module. Plug RS communication module into the slot of the controller. Put back the small cover. Hint: When you insert RS communication module, the boot jumper is hidden. For that reason we recommend to use RS communication module with the boot jumper placed on it. See pictures below: RS communication module with the boot jumper. Connect controller to PC, run LiteEdit and wait until connection bar at bottom turns red.
Select correct firmware and confirm dialog. Than follow instructions in LiteEdit. This is required for computer or Modbus connection. You must open the cover first use screwdriver to open and then insert the module into slot. RS RS Boot jumper RS Terminator jumper Hint: - Boot jumper programming — In case of interrupted programming or other software failure is possible to use the boot jumper programing to restore controller to working order.
Once you have inserted it, part of the module will remain over plastic box. It is supposed to be used as a service tool. When you need to remove it, grab module in cutouts and pull it up manually. Hint: Boot jumper programming — In case of interrupted programming or other software failure is possible to use the boot jumper programing to restore controller to working order.
This card also enables to monitor and control the genset over web browser from any location with internet access using appropriate security measures. Hint: The module requires some settings before initial usage. See IB-Lite Noncompensated gauges like V or mA are not supported. Gauge type and value are configured in LiteEdit software. Any analog value from controller may be shown in that way. PC Installation Suite consist a set of prepared converting curves for basic usage of PWM outputs with automotove gauges.
Through this card controller can accommodate up to 8 binary inputs or outputs. Remote display provides the same control and monitoring functions as controller itself. No further programing of the display is required — unit is self configurable from the main controller.
The module can be also enabled or disabled using LiteEdit software. Hint: Please see the documentation of RA15 for the technical and function description. The module can be used especially for Pt sensors and current sensors. It is connected to controller via RS line. See InteliCommunication Guide for further details. Requested cutout size is xmm. Use the screw holders delivered with the controller to fix the controller into the door as described on pictures below.
See Engines started via CAN bus. General To ensure proper function: Use grounding terminals. Wiring for binary inputs and analog inputs must not be run with power cables. Use copper conductors only.
Grounding The shortest possible piece of wire should be used for controller grounding. Use cable min. Switchboard and engine has to be grounded in common spot. Use as short as possible cable to the grounding point. Power supply To ensure proper function: Use min. Maximum allowable power supply voltage is 39VDC.
When there is a potential risk of the controller being subjected to conditions outside its capabilities, an outside protection devise should be used. Therefore is strongly recommended to interconnect these two terminals together. Hint: The InteliLite controller should be grounded properly in order to protect against lighting strikes!!
For the connections with 12VDC power supply, the InteliLiteNT includes internal capacitors that allow the controller to continue operation during cranking if the battery voltage dip occurs. If the voltage before dip is 10V, after ms the voltage recovers to 7 V, the controller continues operating. During this voltage dip the controller screen backlight can turn off and on but the controller keeps operating. It is possible to further support the controller by connecting the external capacitor and separating diode or I-LBA module: The capacitor size depends on required time.
It shall be approximately thousands of microFarads. The capacitor size should be 5 microFarad to withstand ms voltage dip under following conditions: Voltage before dip is 12V, after ms the voltage recovers to min. Voltage before dip is 12V and after ms the voltage recovers to min. The wiring resistance from battery should be up to 0. Current drain of heating element exhausts LBA capacitors very fast.
Power supply fusing A one-amp fuse should be connected in-line with the battery positive terminal to the controller and modules. These items should never be connected directly to the starting battery. Fuse value and type depends on number of connected devices and wire length.
Recommended fuse not fast type - T1A. Not fast due to internal capacitors charging during power up. Single phase application: Connect CT according to following drawings.
InteliLite NT AMF 25
New generation of one of the world's most successful controllers in its class. Parameters Customer stories Downloads Related products Local distributor. El Katamy rent and sell the generators for both private and governmental companies in the United Arab Emirates and Egypt. Case studies. Case study The Greenest Datacentre in Switzerland. Single gen-set controllers.
InteliLite NT AMF 25 Gen-set Controller (IL-NT AMF25) ComAp
InteliLite AMF 25